Complete underfloor package - for heating max 200 square metres - L-7 package
Package L – 7 for heating 150 – 200 m2.
Ideal for heating of six rooms.
How it works: first, water, which is initially mixed by a thermostatic mixing valve, is charged by a pump and transmitted to thermostatic valves. An impuls from the room thermostat controls - using a thermoelectric actuator – the element of thermostatic valve that directs into the aproppirate circuit the hot water with the optimum flow. Very important is to inlcude in the system a regulation valve using which one should set flow through the shorter circuit as the prevention against the uneven heating of the floor. The package is equipped with a by-pass valve, that leads water into the return in the case of the themostatic valve closing. Additionally, the system is protected by an adjoined thermostat that switches off the pump at the exceedeed temperature (setup temperature for an underfloor heating is 55oC) .
L – 7 package 9 (about 150m2 heating panel) comprises of:
- mixing valve TZM VTA 1“ GZ ESBE – 1 item
- thermoelectrical actuator AFRISO – 7 items
- room thermostat TA 3m IMIT – 6 items
- adjoined themostat BRC IMIT - 1 item
- pump WILO Stars RS 25/7 with couplings
- by-pass valve ¾” AFRISO – 1 item
- electric list - 1 item
- connections – 1 package
- deaerator AFRISO – 2 items
- manifold R7 – 1 item
- detailed assembly instruction – 1 item
- pipe 16 x 2,0 mm HENCO - please choose the required pipe quantity at the bottom of the page